The System Selector below will help you choose the correct system. Simply tick the boxes that apply to your situation. If you want to restrict your search to a single manufacturer, click your choice from the dropdown menu. If you know the identification number of the system you want, click here for a list of systems.
Important Note: Systems tested in plasterboard may also be used in concrete (AS 1530.4 Section 10.12.2). Therefore all the systems shown below with diagrams in plasterboard may be used in concrete. Many systems (tested to EN1366) also are available for timber floors and walls.
Showing systems that use 3M™ Fire Barrier Water Tight Sealant 3000 WT only.
System ID FC282
PEX pipes (single, 16mm to 26mm od) through a plasterboard, concrete, masonry or AAC wall. 3M 3000WT Sealant to a depth of 26mm for -/120/120 with an optional 25mm fillet both sides of wall to give -/180/120. Annular gap max 10mm. May be zero one side.