Cables D1and D2, cable trays, metallic pipes in any combination or blanks through a concrete floor min 100mm slab depth. Max aperture 425x300mm. 3M Composite Sheet CS-195, 1 or 2 layers. Wrap strips, putty and sealant as required - see detailed instructions. Insulation up to 120 by wrapping with E-5A-4 Mat
Fire rating: 240
Thermal rating: 90, increased to 120 with E-5A-4 Mat
Size: Cables including trays, copper < 15mm, steel < 34mm
Below are the downloads available. Please tick the ones you would like to receive and complete your details and select how you would like the files delivered to you. Alternatively you can click on the individual download name to view it now.