Cables D1 and D2, cable trays, blanks or metallic pipes through a plasterboard or concrete wall in various combinations. Wall min 120mm thick. Aperture max 800x600mm. 3M Composite Sheet CS-195 to each side of wall. Wraps and sealant as required. Insulation increased to 120 by wrapping with E-5A-4 Mat.
Fire rating: 180
Thermal rating: 90, or 120 with E-5A-4 Mat
Size: Cables including trays, copper < 15mm, steel < 34mm
Below are the downloads available. Please tick the ones you would like to receive and complete your details and select how you would like the files delivered to you. Alternatively you can click on the individual download name to view it now.