Cables (PVC insulated D1 & D2) and metallic pipes (copper/ferrous < 150mm, brass < 100mm) through a concrete floor min 120mm slab depth. 3M Fire Barrier Mortar from 75mm depth with 3M CP 25WB sealant and 3M Putty Pads for cable bundles. Thermal of 120 available using 3M E-5A-4 Endothermic Mat.
System ID #: 220
Max Fire Rating: 180
Max Thermal Rating: 60, or 120 with E-5A mat
Size: Cable bundles, copper/ferrous < 150mm, brass < 100mm
Below are the downloads available. Please tick the ones you would like to receive and complete your details and select how you would like the files delivered to you. Alternatively you can click on the individual download name to view it now.