Cables (PVC, insulated, type D1 & D2, cable trays), metallic pipes (steel up to 34mm, copper or ferrous up to 15mm) or blanks (300x425mm) through a concrete floor min 120mm slab depth. 3M Fire Barrier Pillows with 3M CP 25WB sealant to gaps in cable bundles and 3M Putty Pads around pipes. Thermal of 120 available using 3M Duct Wrap 615+.
System ID #: 218
Max Fire Rating: 180
Max Thermal Rating: 60, or 120 with Duct Wrap 615+
Size: Cable bundles, cable trays, steel<34mm, copper/ferrous<15mm
Below are the downloads available. Please tick the ones you would like to receive and complete your details and select how you would like the files delivered to you. Alternatively you can click on the individual download name to view it now.