Cables (multiple, with or without cable tray) through a concrete floor (120mm min). 3M CP 25WB+ sealant 40mm deep at top of floor only, backed by 80mm mineral wool. Annular space 25-60mm. Thermal up to 120 available using 3M E-5A-4 Endothermic Mat. Max FRR -/180/120
System ID #: 216
Max Fire Rating: 180
Max Thermal Rating: 30, or 120 with E-5A mat
Size: See info sheet D1 & D2 Cables & Trays
Below are the downloads available. Please tick the ones you would like to receive and complete your details and select how you would like the files delivered to you. Alternatively you can click on the individual download name to view it now.