uPVC (to 100mm), PEX or PEX-AL-PEX gas pipes (to 25mm) through a plasterboard wall, minimum single layer 13mm. Trafalgar FyreCHOKE Collar to each side of the wall with annular spaces between pipe and plasterboard filled with Trafalgar FyreFLEX Sealant to the depth of the plasterboard. Fire rating to match rating of the wall or Max FRR -/120/120
System ID #: 525
Max Fire Rating: 120 minutes
Max Thermal Rating: 120 minutes
Size: uPVC up to 100mm, PEX or PEX-AL-PEX to 25mm
Below are the downloads available. Please tick the ones you would like to receive and complete your details and select how you would like the files delivered to you. Alternatively you can click on the individual download name to view it now.