NZ Building Code compliant AS1530.4-2014 & AS4072.1-2005. Acoustic Rating STC 58.
Designed to maintain the fire resistance of fire rated walls and floors where these are breached by plastic pipes up to 400mm diameter. May be used in plasterboard, masonry or concrete. Pipes may be PVC-C, PVC-U, PE, HDPE, ABS, PP, SAN+PVC, Aquatherm Green or Acoustic (blue drainage).
Each pipe collar consists of a split white coated, circular steel casing designed to fit around plastic pipes. The collars have a secure and simple locking device. The steel shell contains a graphite based intumescent material that reacts to heat and fills the opening from the melting plastic pipe in case of a fire.
For sealing plastic pipes in floors, a single pipe collar is installed on the underside of the floor and for plasterboard and solid walls, a pipe collar is installed on both sides of the wall.
On sites where the penetration size is greater than the pipe diameter or where pipework has a gradient for flow purposes, an oversized collar can be used. Protecta FR Collars are tested ‘oversize’, i.e. the internal diameter of the collar can be larger than the pipe. Any collar up to 160mm can be used oversize on any approved system. See attached Polyseam statement confirming conditions under which an over-sized collar of any dimension may be used to accommodate angled pipes.
Before fitting the pipe collar ensure that any gaps between the pipe and the separating element are filled with a sealing bead of Protecta FR Acrylic. For larger gaps back with mineral wool.
Below are the downloads available. Please tick the ones you would like to receive and complete your details and select how you would like the files delivered to you. Alternatively you can click on the individual download name to view it now.