Cables (D1 and D2 cables as per AS1530.4, including cable trays) through a plasterboard or concrete wall. 3M CP 25WB+ sealant to 20mm to both sides of the wall, with 75mm mineral wool backing. Thermal of 120 available using 3M E-5A-4 Endothermic Mat.
System ID #: 217
Max Fire Rating: 120
Max Thermal Rating: 30, or 120 with E-5A mat
Size: Cables D1 or D2, Cable Trays
Below are the downloads available. Please tick the ones you would like to receive and complete your details and select how you would like the files delivered to you. Alternatively you can click on the individual download name to view it now.